With the application setting Refrigeration & Air Conditioning (AC) the capacity data of the compressor are related to the evaporator (cooling capacity).
With the heat pump application function the capacity data of the compressors are related to the condenser (heat capacity).
Required minimum superheating Δtoh = 20 K
Supplementary cooling or reduced suction gas temperature (Δtoh<20K)
Supplementary cooling and reduced suction gas temperature (Δtoh<20K)
The compressor can be operated within the limits of the applications shown in
the diagram.Please note the importance of the colour shaded areas.A
minimum superheating of Δtoh = 20 K must be maintained for the dark-blue
application range.An internal IHX heat exchanger must be provided for this
if necessary.Thresholds should not be selected as the design point or the
continuous operating point.
Semi-hermetic six-cylinder reciprocating compressor with
drive motor for part winding startSingle-section compressor housing with
hermetically integrated electric motor
Winding protection with PTC resistor sensors. Electronic
triggering unit INT69 G to be fitted in switch cupboard (enclosed)
connection of oil level controllers ESK, AC+R or CARLY
Possibility of connection of oil level controllers Traxoil 5)
Oil charge:HG HC: FUCHS Reniso SYNTH 68
Internal safety valve
Suction and discharge line valve
Inert gas charge
4 anti-vibration pads enclosed